Minattitland4000kva power transformerIndustry development injects new momentum
release time: 2022-03-01 09:25:15
Causes of fire in power transformerIn order to better carry out the experiment of power transformer oil, it is necessary to sample the power transformer oil. The sampling work should be carried out on a dry sunny day. The commonly used containers and sampling methods during sampling do immediate harm to whether the specific quality of the oil can be truly reflected. The oil sample for AC voltage withstand test shall not be less than .kg,MinattitlandOverload capacity of oil immersed transformer, and the oil sample for simplified experiment shall not be less than kg.Minattitland,Transformer isThe power transformer conductor refers to the connecting transmission line between each electromagnetic coil, between the electromagnetic coil and the group outlet pipe, and between the electromagnetic coil and the tap changer.Gargzdai,The time difference between different steps of three-phase power switch of switching power supply shall be less than ms, the closing shall be maintained by high-voltage arrester, and the neutral line of transformer shall be reliably grounded (it shall be grounded immediately).Equipped with a temperature controller,MinattitlandAllowable temperature and temperature rise of oil immersed transformer, stop the cooling centrifugal fan, set up common problem alarm overtemperature alarm and overtemperature tripping effect, and provide reliable overvoltage protection machinery and equipment for the dry test transformer, so as to test the safety performance of the transformer operation.The insulation distance between the winding and the iron yoke of power transformer is much larger than that between the windings because the electric field between the winding and the iron yoke is far away and not as symmetrical as that between the windings. In the electric field in the middle of the winding, most of the cables are in phase with the insulating cylinder (plate) in the middle of the winding, that is, the disconnection component of the electric field is small.
After tightening the loose bolts, seal the flange, and solve the bolts that are likely to leak, so as to achieve the goal of complete treatment. Tighten the loose bolts strictly according to the actual operation and processing technology.Many people probably don't know much about the power distribution transformer manufacturers. In fact, the transformer can be plugged in for trial operation after careful inspection before capital investment. During the trial operation period, you must pay attention to the following points. Whether there is abnormal sound, noise and vibration, whether there is abnormal smell such as coke smell, and whether there is discoloration caused by partial overheating. Ventilation is good. In addition, we should also pay attention to the following aspects.Dry type transformer companyManagement Department,When the transformer is put into operation, if the tap changer is not in time, a great & ldquo; Tweet & rdquo; The high-voltage fuse is broken when the noise is serious; If the tap changer is defective, it will cause mild & ldquo; Squeak & rdquo; Corona discharge sound, once the load increases, it is likely to burn the circuit breaker of the tap changer. In case of such situation, power off immediately for maintenance.Insulation and heat removal are different. Dry type transformers are generally insulated with epoxy resin, insulated by insulating oil in the circulating system inside the transformer, and heat is discharged on the radiator (radiator) of the circulating system inside the transformer.Loose core screw
In the electric field of the winding to the yoke, there must be a strong line breaking component, so that sliding flash charge and discharge may occur at a lower current. In order to better solve this disadvantage, the appearance of the insulating parts between the winding and the iron yoke should be the same as that of the medium horizontal plane of the winding to the iron yoke insulation as far as possible, so as to reduce the electric field component intersecting with the insulating parts.Economic management,The insulating layer in the middle of the silicon steel plate is aging, the iron core causes large vortex,MinattitlandLandscape box transformer, temperature rise, and the aging of the insulating layer is accelerated. The core insulation compressive strength of power transformer must be measured on time and accurately. If it is found that the insulation compressive strength is less than the index value, please remove and replace the anchor bolt cover or carry out insulation for the copper core cable.Many people probably don't know much about the power distribution transformer manufacturers. In fact, the transformer can be plugged in for trial operation after careful inspection before capital investment. During the trial operation period, you must pay attention to the following points. Whether there is abnormal sound noise and vibration, whether there is abnormal smell such as coke smell, and whether there is discoloration caused by partial overheating. Ventilation is good. In addition, we should also pay attention to the following aspects.After the oil is drained, all anchor bolts of the automobile oil tank at the upper end of the detachable oil cover shall be tied with the lifting jack, and the lifting point shall be on the common earrings or bolts. If necessary, the human resources traction belt shall be used as a guide.Minattitland,Operation of oil immersed transformerGenerally speaking, the ignition emergency treatment method of oil immersed transformer is mainly to disconnect the oil immersed transformer, disconnect the switching power supply on each side, quickly invest the reserved oil immersed transformer and start the power supply system from scratch. Stop the operation of refrigeration equipment. Key oil immersed transformer ignition. When L-type oil immersed transformer and high voltage station oil immersed transformer are ignited the generator set must be disassembled first.When sampling in bulk gasoline barrels, samples shall be selected according to % of the number of gasoline barrels, but not less than barrels. When sampling in batches of small and medium-sized pails or bottles, samples shall be taken according to % of the total number of barrels (bottles).
The content of the entry is for reference only. If you need to solve a specific problem (especially in the fields of law, medicine, etc.), it is recommended that you consult professionals in the relevant fields.
If you think this entry needs to be improved, please edit
Previous Constant springDry type transformer sizeAnalysis of the causes of wear and countermeasures Next Pidras nigrasS13-50 / 10 power transformerWhat kind of standard is the production based on