DimonaPower saving transformerHow to check the accuracy of machining work
release time: 2023-03-19 06:58:30
Dry type transformer manufacturerThe long-term overload of power transformer will slowly cause the scalding and insulation aging of solenoid coil, resulting in short circuit between coils two-color short circuit or short circuit on the ground, resulting in the ignition of power transformer. Therefore, and overload is not allowed in the whole process of operation.Dimona,Under normal conditions, different oil-based oils cannot be mixed. Under special circumstances,DimonaOil immersed high voltage test transformer, if it is necessary to use new oil of different grades, it should be determined whether the mixed oil with ice degree can be used according to the requirements of the region, and then the oil mixing test should be carried out.Avoid inadvertent damage of insulation during maintenance: when repairing the hanging core of power transformer,DimonaElectric box transformer, special attention shall be paid to the maintenance of solenoid coil or insulating waterproof sleeve. If there is scratch damage, it shall be handled properly.Novo Mesto ,Oil immersed transformer operationTherefore, in the operation prevention and regulation of relay protection dry-type transformer, it is necessary to find the short-circuit fault point according to the fault situation, lock the fault point, and analyze the short-circuit fault types of relay protection dry-type transformer. At the same time, if all fields are clear, disconnect the switching power supply at the fault point, the maintenance work of employees will be carried out smoothly and the harm will not expand to a greater extent.For the leakage that has already occurred, find the leakage point first, which can not be ignored. For the position with serious leakage, the treatment surface shall be cleaned and tidy. Polymer composite materials are mostly selected for dry consolidation. After dry consolidation, the goal of long-term treatment of leakage can be achieved.
Insulation and heat removal are different. Dry type transformers are generally insulated with epoxy resin, cooled by natural air and large capacity by centrifugal fan. Oil immersed transformers are insulated by insulating oil, insulated by insulating oil in the circulating system inside the transformer, and heat is discharged on the radiator (radiator) of the circulating system inside the transformer.The transformer manufacturer said that the selection should be based on the application environment of the dry-type transformer. For the extremely extreme environment, the dry-type transformer should be poured with epoxy resin glue. Because this kind of environment does not need to heat the dry-type transformer, it can operate immediately. However, for the general application environment, the class H dry-type transformer can be used.What is the reason for the shutdown of power transformer?Honest management,Generally speaking, the ignition emergency treatment method of oil immersed transformer is mainly to disconnect the oil immersed transformer, disconnect the switching power supply on each side, quickly invest the reserved oil immersed transformer and start the power supply system from scratch. Stop the operation of refrigeration equipment. Key oil immersed transformer ignition. When L-type oil immersed transformer and high voltage station oil immersed transformer are ignited, the generator set must be disassembled first.Power transformer plantFalling foreign matters and piercing
When the power transformer operates at full load it needs a large reactive load. This reactive load shall be provided by the power supply and distribution system. If the transformer volume is too large, it will not only increase the initial project investment, but also make the transformer operate at full load or load for a long time, expand the proportion of full load loss, reduce power factor and increase Internet loss. Such operation is neither economic development nor scientific.Customer first, it shall be installed between the disconnector and low-voltage composite insulator, or the circuit breaker shall be selected as the disconnector; If there is no disconnector on the secondary side, it shall be installed on both sides of the low-voltage composite insulator, and the insulated cable jumper shall be connected to the insulated cable on both sides of the circuit breaker.During the operation of the transformer, the resistance value of the grounding wire shall be measured accurately every two years.For example, in the s, the radio programs applied by every family in the countryside had a ground wire, and they were often wet with tap water. Protective grounding is to bury the copper plate of metal electrical conductor in the soil layer, and then lead a point of it out of the road with transmission line, which completes the grounding protection. The grounding wire specifies the grounding wire resistance ≤ Ω. Grounding protection is a safeguard measure adopted to avoid safety accidents when using household appliances, office and other electrical equipment.Dimona,When the screw of the through core extruder holding the iron core of the transformer is loose, there are screw cap parts left on the iron core or small metal materials fall into the transformer, the transformer will send out & ldquo; Ding Ding Dang & rdquo; Or & ldquo; Call & hellip; Call & hellip& rdquo; Blowing sound and its & ldquo; Squeak, squeak & rdquo; It's like a magnet sucking a small washer, while the working voltage, and can be solved until power failure.Then clamp the branch pipe with your thumb, clearly put forward the glass test tube, rotate and release the oil in the tube to clean the sampling tube, carry out it twice, and then draw the oil sample.What is the reason for the shutdown of power transformer?
The content of the entry is for reference only. If you need to solve a specific problem (especially in the fields of law, medicine, etc.), it is recommended that you consult professionals in the relevant fields.
If you think this entry needs to be improved, please edit